Our company's main products include gas&oil-fired boiler , coal-fired boiler , biomass boiler , thermal fluid heater and other series with more than 400 varieties of specifications.Know More About Products →
1. The air in the economizer and condenser has not drained yet when firing. The safety valves of economizer and condenser need to be turned on to exhaust steam. Return pipe valves also need to be turned on, enabling the steam in the economizer and condenser to return to softened water tank.
2. The outlet water temperature is so high that economizer and condenser will have vaporization phenomenon. The outlet water temperature of economizer and condenser need to be controlled.
3. The check valve of the inlet of economizer and condenser is not at normal conditions. The check valve needs to be repaired.
The life of the heat medium oil for thermal fluid heater is related to the operating temperature, and the life is shorter when the operating temperature is high.
After half a year, the heat medium oil is used for sampling every 2-3 months. When the flash point of the heat medium oil changes by more than 20%, the acid value is less than 0.5 mgKOH/g, and the residual carbon is less than 1.5 wo/o, when the color of oil becomes dark, it indicates that it has failed and needed to be replaced.
LEAVE YOUR MESSAGE !
7*24 hours of counseling service, offering the most effective and fastest service to ensure that the loss caused by the failure for customers is minimized.